The Dust Removal Centrifugal Fan is an equipment for discharging air mixtures containing dust, wood chips, fine fibers and so on. The Dust Removal Centrifugal Fan can also be used as a general fan, such as the discharge containing hard particles, must be in the fan inlet before the addition of dust removal device.
The Dust Removal Centrifugal Fan formation single suction, machine number of three. The Dust Removal Centrifugal fan is made into right-handed and left-handed forms. From one end of the motor facing, the impeller clockwise rotation, known as the right - hand fan. To the right;Rotating counterclockwise is called a left cyclone, denoted by "left". The outlet position of the fan is indicated by the outlet Angle of the housing. The adjusting range is between 0 ° ~ 225 °. Left-handed and right-handed fan can be made from 0 °, 45 °, 90 °, 135 °, 180 °, 225 °, a total of 6 kinds of Angle.
The Dust Removal fan is driven by v-belt. If the user has a change in pressure and flow requirements, according to the provisions of the performance table, self- adjustment.
Air flow range
The Dust Removal Centrifugal Fan is mainly composed of impeller, air inlet, housing, transmission part and motor.
1. The impeller. The 10 reclining aerofoil blades are welded between the cone cover and the plate wheel. Blade, wheel cover and wheel disc are all made of 16Mn steel. The whole impeller runs smoothly through dynamic and static balance correction.
2. The chassis. The cochlear shell is welded by ordinary steel plate. The installation and disassembly of the impeller shall be carried out by one side of the housing。
3. The air inlet is made into a collecting streamline integral structure. Install it on the side of the fan.
4. The transmission part consists of the spindle, bearing box, rolling bearing and belt wheel. The spindle is made of high quality steel. The overall structure of the bearing box adopts rolling bearing. Rolling bearings are lubricated with calcium - sodium base grease.